I like to figure out 'stuff' and I wondered why a splice for a 10-8 awg wire was provided for a 18-14 awg wire?
I was getting an Under Voltage message and the generator would shutdown. It took some thinking about what the message was actually telling me and several hours of testing to find out it was the splice. I replaced it with the correct size and it has been great since.
Pros:I'd Buy It Again
George Recommends This Generac Product
We always suggest having an installation performed by a certified electrician or Generac installer.